Learn when a reed bed can be used for leachate treatment, and when the more expensive choice of a more high-tech leachate solution will be needed, such as a Sequencing Batch Reactor Leachate Treatment Plant.
Tag Archives | leachate treatment plant
“Making a good choice whether to Install Reed Beds or Biological SBR Treatment Processes for Treating Landfill Leachate”
The question often arises for landfill operators, of whether to use a “SBR” Leachate Treatment Process, or if the cheaper alternative of a reed bed can be used.
The answer is that it depends entirely on the strength of the contaminants in landfill leachate. The first choice, when enough land is available to site a reed bed, is the use of low running cost, low energy consumption, reed beds.
However, simple reed beds designed to be fed with leachate as horizontal flow type, engineered wetlands have a limited application for landfill leachate, because these traditionally laid-out reed beds can only be used for very dilute leachate from the very oldest landfill sites. These are sites which were built before the adoption of sanitary (lined) landfill practise, where the leachate is at its weakest.
These landfills where reed beds alone can be used for leachate treatment are usually those landfills which are not lined nor capped, and located in temperate and wet places. This means that their leachate is substantial diluted, and old, and has been weakened by the addition of groundwater and rainwater entering the landfill. These would have been called tips or dumps in their day.
Modern “sanitary” (lined and capped) Municipal Solid Waste (MSW) Landfills invariably have a much more heavily contaminated and “fresher” (more acetogenic) leachate, and a more high-tech treatment system then becomes essential.
For many landfill operators the most successful method a leachate treatment for the past 30 years has been the biological aeration of a microbiologically active sludge, and this is followed by a anoxic phase reaction known as denitrification, where removal of total nitrogen is required.
“If a reed bed won’t do the job, an SBR, or nitrification followed by denitrification type system, is the next option to look at in most cases”, Leachate Expert, Steve Last of IPPTS Associates said.
A common feature of such process designs is that they are “sequencing reactors”, which simply means that they are run by computer controls, on a batch process system. The computer is used to automatically control the periodic feeding of leachate, aeration, chemical dosing, and discharge of each batch, etc.
Plants like this have become known as simply “SBRs” (Sequencing Batch Reactor Plants), in the leachate treatment industry.
SBR Plants, usually with a denitrification stage, can be configured to:
- discharge it directly to a river or stream, usually via a reed bed which is used as a final polishing process stage. In which case the plant will need to treat the leachate to a high quality, or
- they may alternatively only pre-treat the leachate to remove a proportion of the contaminants, before discharging it for further treatment into a public sewer. In such cases the receiving sewage works provides the necessary additional treatment.
When to Install Reed Beds or Biological SBR Treatment – SBR Leachate Treatment Process Description
The simplest SBR landfill leachate treatment plants use the biological aeration (nitrification) process in a single tank or lagoon.
These plants work automatically to run each batch filling of leachate through its treatment cycle.
Once every predetermined time interval of from 6 hours to a day or more depending on the raw leachate strength and the discharge effluent quality needed, to satisfy the requirements of the local environmental regulating body.
More than 50 SBR landfill leachate treatment plants have been constructed to designs by Last, Robinson and Olufsen, in many countries worldwide, and original plants have been in operation for in excess of 20 years. SBR landfill leachate treatment plant technology is now thoroughly tried and tested, and a wide range of operational data on such plants while in operation, has been reported in published papers.
The design of this type of SBR is similar in principle to the activated sludge process, which until recently was the process adopted for almost all wastewater treatment works (sewage works). In an SBR, similar aerobic reactions occur. Similar microorganism do the work of “treatment” in the tanks of both systems.
But, there are important differences between sewage and leachate, and the most important difference is the far higher ammonia (ammoniacal-N) in leachate, so that is where the similarity ends.
In fact, the activated sludge process as used by designers of sewage treatment works, suffers from the problem that it becomes unstable when treating the high ammoniacal-nitrogen concentrations in full strength sanitary landfill leachates.
Perfectly well experienced sewage treatment process experts have many times come unstuck, when making attempts to modify sewage works type activated sludge treatment systems to adapt sewage works designs for use in leachate treatment.
Activated sludge wastewater processes which have been used to treat leachate cannot match the robustness of a well-designed SBR/ nitrification/ denitrification process, provided by a leachate treatment expert experienced in leachate treatment plant design.
Most people in the landfill industry say that leachate is hard to treat. But, that sentiment comes from the large number of failed leachate plants which have been designed as if leachate was somehow comparable with sewage, and in that the mis-judged use of reverse osmosis (RO) Plants can also be considered a factor.
However, use of the SBR nitrification/ denitrification process, when applied correctly, often in combination with RO and/or ultrafiltration offers a robust and as stated previously proven technique for the treatment of strong leachate from all modern sanitary landfills.
Other processes may be required depending on the local environmental regulator’s requirements for such higher quality water at the discharge point as local conditions, and national regulations, may dictate. These may include:
- Membrane Processes
- Dissolved Air Flotation (DAF)
- Activated Carbon Filtration.
A stated earlier, as well, in many examples these are provided in combination with a compact reed bed which provides polishing of the effluent to a very high level of purity, and provides a process performance buffer, before the treated water enters the natural environment.
The SBR Treatment Cycle and features (in a simple nitrifying SBR) are:
Feed and fill the tank/ reactor
- Minimise energy use through control of aeration rate and aerator run-time duration, throughout the aeration period in each cycle
- Settle the contents by waiting for the particles to coagulate and fall to the bottom
- Open a valve and draw-off the clean water off the top of the tank.
Secondary clarifiers for particulates removal are not needed in many cases, and therefore a compact footprint is possible.
The removal of pollutants is achieved by biological action, requiring a very minimum of chemical addition, and this is achieved through
- Close monitoring and supply adjustment for pH control and oxygen demand adjustment
- Robustness in operation arising from the large water volume stored in the reactor tank(s)
- Minimising and absorbing shock leachate flow and high strength loadings;
- Economic operation under normal low dry weather flow/ loading conditions but readily adjustable to operation at a higher flow per cycle of operation during extended wet weather periods;
The SBR process, also operates with minimal sludge generation for most leachates, so there are none of the large sludge disposal cost of some other designs.
So, you now should have found out when to Install Reed Beds or Biological SBR Treatment.
- Robinson, H.D. Olufsen, J.S. and Last, S.D. (2005). Design and operation of cost-e=ective leachate treatment schemes at UK landfills: Recent case studies. Published in the CIWM Scienti%c and Technical Review, April 2005, pp 14-24 © 2005 IWM Business Services Ltd.
- Other Published Conference Papers:
- CIWM Scientific and Technical Review, April 2005, 14-24. ROBINSON H D, FARROW S, CARVILLE M S, GIBBS L, Operation of the UK’s Largest Leachate Treatment Plant 6 Years of Experience at Arpley Landfill, Roberts S J and Jones D. Paper presented to XII International Landfill Symposium Sardinia, October 2009, 10pp
- Robinson H.D., Farrow, S., Last, S.D. and Jones, D. (2003). Remediation of leachate problems at Arpley Landfill Site, Warrington, Cheshire, UK. Paper presented to XII International Landfill Symposium Sardinia, October 2003, 10pp, 10pp
Need Help with your Leachate?
We provide leachate consultancy advice for all landfill leachate requirements.
Whether you have a new landfill which needs a leachate plant, or you simply have problems with an existing leachate management system, we can help.
Construction has started on the world’s most expensive leachate treatment plant which at $27 million will be the most expensive ever built in the world to date. A number of plants are estimated to have been built at up to $15 million previously, but this one is significantly the most expensive in terms of the […]
Air Ammonia Stripping is a leachate treatment process which is now largely outdated and seldom used. During the 1980s in the United Kingdom it was seen as a potential physico-chemical leachate treatment process which would be suitable for the treatment of leachate from sanitary (lined and capped) landfills, however, although a number of pilot scale […]
First of all when asked the question, “How Do You Treat Leachate?”, we would like to make a distinction between true treatment which involves converting environmentally damaging substances to less, or non-toxic, ones, and simply concentrating the contaminants from the water in leachate to give a volume reduction. In the water industry both are known as […]
Download our FREE time saving calculator which is intended for use for trade effluent discharge cost assessments for England, Wales and Northern Ireland in respect of sewer discharges. The Free Trade Effluent Charges Calculator software will be useful for anyone making an industrial effluent discharge to a sewer, and who wants to know how much […]
We plan to add a number of leachate software applications to this page over the next few months, which our visitors can download and install, and which will provide solutions to a number of problems experienced by leachate treatment plant operators. Our first two are now available, a handy conversion calculator (see below), and (see right) our Trade Effluent Charges Calculator here.
Ammonia to Ammoniacal Nitrogen “Expressed as N” – Free Conversion Calculator
There are two methods used by analytical laboratories for expressing the quantity of ammonia in contaminated water. The first is that provided bythe majoirty of water quality analytical laboratories when reporting the quality of a polluted water. They provide a weight of ammonia as the weight of the nitrogen (elemental N), “ammoniacal- N” and that is the method used by the Enviroment Agency UK.
However, some water quality labs report the weight of “ammonia”, (ie the whole NH4 molecule) which includes the weight of the hydrogen atoms as well as the nitrogen atoms, and landfill site operators may at times erroneously think that they are closer to their maximum permitted ammoniacal nitrgen strength for discharge, than they really are.
To help landfill operators correct for the difference between the two methods of expressing ammoniacal nitrogen values we devised the software below, which will walk you through how to calculate Ammoniacal-N (ammonia expressed in mg/l as N) concentrations (as used in UK Trade Effluent charging and dicsharge consents and environmental permits).
Get started now using our software, in three steps, as follows:
1. Simply download the zipped file below and unzip it into its own new directory location on your hard drive where you will be able to go back to it later.
2. Double click on the executable file (file extension “.exe”) called “ammonia-converter.exe”, and the software will load up and you can start to use it.
3. Follow the instructions given inside the software program.
For your free software DOWNLOAD click here >>>Ammonia to Ammoniacal-N Converter Software Package Version 1
Please give us your feedback by filling in a comment below about our Ammonia as Nitrogen (N) converter software, and if we like your suggestions we may be able to incorporate them into a later version.
“The person who walks with his/her eyes on the stars, is susceptible to the puddles in the road.” We all would like to follow our stars, but at times we need to do some “puddle watching” too! Sometimes we need to know what not to do, what things and actions to avoid, and why…
When designing any leachate management system the assessment of the most economic method for leachate treatment and disposal is heavily dependent upon the flow rate and duration of flow. A high capital cost option such as on site leachate treatment will be worthwhile, but only if the total volume the plant treats daily is sustained […]
If you would like us to provide you with:
- General feedback and questions about leachate, or
- A proposal and costs for a leachate treatment plant design,
please use the form below.
Please provide as much of the information requested on the form below as possible, to enable us to provide our feedback reply, or proposal, efficiently.
If you wish to contact us for anything other than a leachate treatment plant design, or feedback about leachate management and treatment designs, please use our general Contact Form here.